Watercolor images are among the most vulnerable artefacts to the effects of firefighting water systems.
According to the NFPA 750 definition, watermist is a water spray for which the 99% of the total volume of liquid (Dv0.99) is distributed in droplets with a diameter smaller than 1000 microns at the minimum design operating pressure of the water mist nozzle.A slightly different definition has been introduced by the CEN/TS 14972, as a water spray for which the 90% of the total volume of liquid (Dv0.90) is distributed in droplets with a diameter smaller than 1000 microns at the minimum design operating pressure of the water mist nozzle. Continue reading “Water Mist and Cultural Heritage: can Simulation Tools help assessing its effect?”
In the final Report of the Cost C17 Action different aspects of fire protection of Cultural Heritage buildings have been addressed, as the water mist for fire protection, which at the time was a relatively new technology with specific advantages to the built heritage.
The standard design and manufacturing processes do not currently address heritage applications, but performance-based codes are favourable for introducing new water mist systems. This report establishes the current level of experience, and presents basic information about water mist for the heritage community. The challenges, implications and perspectives of the technology are outlined in order to ensure the best protection of European heritage. A guide on how to accept or approve mist systems in heritage properties is given. Continue reading “Water mist for Protection of Heritage – Cost C17 Final report”